category：Machinery and industry equipment / date：2022-06-23 09:56:46 / browse：85 / comment：6
The clock expression is used to indicate the phase difference correlation of the working voltage of the secondary side line. The phasor of the working voltage of the primary side line is used as the minute hand, and the phasor of the phase voltage of the secondary side is used as the second hand.Fault judgment of power transformerSanta Cruz,Once the insulation material of electrical equipment is overheated, the surrounding gas will cause a kind of odor. This kind of odor can be sniffed out by normal patrol staff. When you smell such odor during normal inspection, you should carefully inspect the equipment and parts until you find out the cause.& ldquo; of wiring transformer; Enter & rdquo; And & ldquo; Output & rdquo; Use a megger to test the grounding resistance between the terminal and the ground wire. When accurately measured by V megger, the resistance value exceeds m ohm bus.Santa-Cruz-del-Quiche,What is the wiring mode of dry-type transformer?High voltage fuse of transformer breaks one phase;The vibration reduction of the grounding device sheet solves the problem of modifying the fixed hard connection between the copper sheet of the grounding device and the dry-type transformer. The original oscillation of the dry-type transformer will be transmitted to the metal in the concrete by the baffle and cause low-frequency noise. Therefore, it must also be changed to produce flexible connection.
Analysis of common faults of oil immersed transformer:First of all, although dry-type transformer has strong moisture resistance, it is generally open structure or very susceptible to moisture, the dry-type transformer can obtain high stability only when the air humidity is below %. The dry-type transformer shall also be prevented from stopping operation for a long time to prevent serious damp. When the grounding resistance value is less than / V (operating voltage), it indicates that the transformer is seriously damp, and the trial operation shall be terminated.In relay protection dry-type transformer the disconnection of the fault point is related to each other. In a word, if there is any problem at a certain point,Santa CruzS11 dry type transformer manufacturer, it will affect the whole power circuitProduct survey,The input and output three-phase power lines shall be connected to phase a, phase B and phase C respectively according to the color of yellow, green and red bus duct of transformer terminal board. The zero line shall be connected to the neutral zero line of transformer voltage, and the grounding wire,Santa Cruz1000 kV Transformer, transformer casing and its transformer point shall be connected to each other. At ordinary times, the ground wire and zero wire are led out by the neutral wire of the transformer. (for example, the transformer box shall be matched with the ground wire mark of the shell and connected with each other). Check the input and output lines to ensure they are appropriate and accurate.Plug in the power with full load first, observe and detect that the input and output voltage meets the regulations. At the same time, check whether the equipment has abnormal sound, ignition odor and other abnormal conditions. If there is any abnormality, please cut off the input switching power supply.Avoid the load operation of power transformer: if the load operation is long-term it will lead to the scalding of solenoid coil, slow aging of insulation, short circuit fault between boxes, two-color short circuit fault or short circuit to ground fault and dissolution of oil.
The vibration reduction of collecting and townhouse solves the soft connection of collecting and townhouse. For the copper bar of the low-voltage bus of the equipment,Santa CruzInspection items of dry-type transformer, the electromagnetic induced noise oscillation may be transmitted from the townhouse to the building structure. The core of noise reduction solution must be changed to copper wire connection.offer,Caused by sand holes and cracks. For crack leakage, drilling stop hole is a good way to remove in-situ stress and prevent widening.Two point grounding device of iron core caused by residual welding scar;The conductor insulation of power transformer is the main part of internal insulation. Some conductors should pass through the middle of electromagnetic coil, or between electromagnetic coil, iron yoke clamp and automobile oil tank wall. Therefore, it is necessary to ensure that this kind of conductor has sufficient insulation compressive strength, i.e. insulation spacing.Santa Cruz,When the screw of the through core extruder holding the iron core of the transformer is loose, there are screw cap parts left on the iron core, or small metal materials fall into the transformer, the transformer will send out & ldquo; Ding Ding Dang & rdquo; Or & ldquo; Call & hellip; Call & hellip& rdquo; Blowing sound and its & ldquo; Squeak, squeak & rdquo; It's like a magnet sucking a small washer, current and temperature of the transformer are all normal. Such conditions generally do not endanger all normal operation of the transformer, and can be solved until power failure.Operation of oil immersed transformerFalling foreign matters and piercing